Earth Notes: Historical Stats to 2014/07
(See the current-day data.)
This page shows historical stats, when available.
See complete historial stats from 2007/10 to 2014/07 when k8055/SheevaPlug were decommissioned.
K8055 log format
YYYY MM DD HHMM timestamp;digital;analog1;analog2;counter1;counter2.
Equipment Change/Upgrade Notes
These should be read alongside the numbers above:
- 2014/07/21: (9:35am) SunnyBeam continuously plugged in as an experiment; expected ~150mW extra load (partly because display is permanently on.
- 2014/07/20: RPi +B ~1.5W typical power draw measured from upstream of 12V-to-5V converter.
- 2014/07/16: SheevaPlug tentatively off 21:33BST, with RPi providing services.
- 2014/07/13: official battery voltage monitoring now on RPi and live power monitoring has been added with high-side AdaFruit INA219 I2C board.
- 2014/07/11: moving services from SheevaPlug to RPi; removed ADSL dump load for now.
- 2014/06/08: increased the basic battery/power sampling interval from 2m to 10m, with intermediate (5m) samples taken and logged when extra energy likely available (eg not overnight or mid-winter).
- 2014/05/04: moved outside (OpenTRV) sensor from inside shed where it was getting rather warm, to porch out of direct sunlight (~3pm); may be ~2°C higher than EGLL temperatures. Bruno's screw slots worked just as designed! Updated s/w on all nodes 8pm--9pm which caused interesting temperature wobbles.
- 2014/04/27: ADSL auto-off-grid hardware finally wired up today after keeping an eye on s/w control behaviour for a while.
- 2014/04/26: all OpenTRV sensors now collecting data, including new one outside under cover.
- 2014/04/10: large (weeping willow) tree more or less due east of us ~30m taken down today; may get less shadowing and thus more generation in the early morning through the summer.
- 2014/03/16: ADSL off-grid given SLA bank showing sign of decent charge (including float); considering auto-changeover between mains and off-grid using latching relay (eg RS 686-7212 / Omron G6EK134PSTUS5DC) on mains side and possibly DC side also controled by digital outputs under main system s/w control or on basis of (say) 13V/14V thresholds and PICAXE/AVR control. Manually switching on/off grid as necessary for now.
- 2014/03/16: note that 60Wp extra 'winter' panel set not deployed this winter.
- 2013/07/07: removed some wire-OR diodes where panels already have built-in blocking diode and leakage/failure of wiring/diode/panel seems low-risk; may be good for a few % more output when feeding MPPT controller, eg as much as 0.7V/14V.
- 2013/07/07: ADSL back off-grid (for a couple of weeks) after a couple of good sunny days and more predicted (will need taking off for poor days and/or SSR-driven mechanism eg to drop mains input so reg uses 12V when not at 14V for a day).
- 2013/07/01: SLA seems to be struggling with ASDL + SheevaPlug load, so ADSL back to mains for time being.
- 2013/06/25: reconnected dump load for LiFePO4 battery and un-parked MotorWind turbine upstream of LiFePO4 battery. Also transferred SheevaPlug and ADSL modem off-grid (~0.3kWh/d).
- 2013/06/24: reconnected LiFePO4 battery; having to assume that C- is (-ve) charge and D- is (-ve) discharge. Secondary voltage sense line and power to desk also reconnected.
- 2013/06/21: primary 12V panel set reconnected to charge controller and thus batteries (and primary voltage sense line); battery state LED moved from amber to green shortly thereafter. Rest of system will be reconnected over next few days.
- 2013/06/16: 12V system still not restored after building works, and MPPT charged showing red for connected old 40Ah gel, so made direct connection from ~24Wp on shed to charger and reconnected main gel set to charger also.
- 2013/04/29: temporarily taking SheevaPlug and ADSL on-grid and disconnecting panels/controllers/etc, for rewiring.
- 2013/04/21: put away nominal-60Wp winter off-grid PV panel set.
- 2013/04/11: ADSL modem/router taken off-grid this evening; ~0.25V drop (non-drooping) in overnight LA battery voltage, presumably from cable losses.
- 2013/01/26: noticed that solar controller amber LED was lit mid-morning with SLA voltage ~12.2V; sunshine forcast for a good chunk of today and tomorrow and voltage already showing ~12.7V on charge. Server has stayed off-grid so far this winter.
- 2013/01/01: lowered LiFePO4 upper threshold to 13.1V to allow for more measurement noise and the fact that it is 'sacrificial'.
- 2012/11/30: winter ~60Wp amorphous panel set put out after run of dark weather and SLA battery consistently under 13V overnight.
- 2012/10/05: ADSL modem moved on-grid until spring on the basis of SLA @ 12.3V at 9am and only intermittent sunshine forecast over next week or so. (Immediate jump to 12.6V after!)
- 2012/09/14: finally installed Maplin N27JL 40W 12V amophorous panel in afternoon via own 5A Si diode; may want to shorten/fatten connection cables at some point to minimise losses.
- 2012/09/05: given another day with the SLA voltage only reaching ~13.2V (@<25°C) I have experimentally removed the ADSL modem load (back on grid instead) to see what difference that makes beyond instant 0.2V rise. Tightened all connections for external and internal screw-blocks (nothing was worryingly loose this time). Note that as of today only 60Wp Unisolar panel and MotorWind are charging the LiPO4 battery with everything else directed to the SLA. (Just after noon 2 days later SLA voltage at ~14.4V ie getting good charge.) Taking back off grid morning of 2012/09/09 at least briefly as SLA battery has been at 13.2V all night. I'm currently of the opinion that the ADSL's power management had stopped working properly and power cycling it is the main fix, but giving the SLA a good charge was fine anyway.
- 2012/09/04: some evidence of poor connections from 100Wp panel (poor charging even in good sun, silly/low voltages at connection box; seemed better after breaking and remaking in-line connections, but will need monitoring.
- 2012/08/05: removed dead 12Wp panel (nearest house, likely to capture least energy anyway) from front porch / shed roof 36Wp set currently running to LiFePO4 as spotted 2012/02/21. Attempted to clean two remaining panels and also very slightly increase tilt of one now nearest the house.
- 2012/07/25: adjusted SLA 'high and charging' down further to 13.2V (from 13.3V) to allow for temperature/voltage compensation at ~30°C ambient.
- 2012/07/08: adjusted SLA 'high and charging' down further to 13.3V (from 13.4V) to allow for temperature/voltage compensation.
- 2012/07/07: bought Maplin N27JL 40W 12V amophorous panel £80 (ie £2/Wp) on offer to install vertically on south-facing wall in September.
- 2012/06/17: retightened all connections, topped-up stand-alone 3.2Ah SLA direct with 1.5W panel in sunshine to ~13.1V, adjusted SLA 'high and charging' to 13.4V (from 13.5V) as previously slightly too conservative I think.
- 2012/05/13: put away 'summer' 60Wp amorphous panel set connected to SLA for the summer.
- 2012/03/15: ADSL modem moved off-grid until autumn; SLA voltage now seen dipping below LiFePO4 ~0.2V at night.
- 2012/02/21: systematically tightened all terminal-block connections because observed deep voltage dips/sags suggested poor connections and high-resistance somewhere. Found one very loose (SheevaPlug ground) and plug rebooted at some point suggesting at least one very bad connection that did indeed need fixing. Noted also that one 12W panel at front seems to be dead.
- 2011/12/11: measurements at noon show voltages at wiring centre 13.05V, but 12.65V at sensor wire terminals upstairs and reading via k8055 as 12.6V/12.7V, which suggests higher sensor input impedances may be needed for accuracy (and battery drain not as dire as advertised), so adjusting pots ~12:50 to get true reading as at voltage probes downstairs, not locally, so about 2% high locally given 1kΩ probe resistance and 50kΩ input pots in series. At 15:30 reading 12.6V/12.7V on k8055 vs 13.0xV downstairs possibly due to drop in 0V side, so have tweaked a little further to compensate. As of 2011/12/14 just after sunny noon reading of ~14.9V (LA) and ~13.6V (Li) corresponded to ~14.5V and ~13.3V at the wiring centre/probe.
- 2011/12/05: used sensor wiring already in place to measure battery voltages closer to source (yellow for Li, red for LA) via 1kΩ resistors tapping wiring centre downstairs, to suffer less from the voltage drop to SheevaPlug at higher supply currents. May require voltage threshold adjustments.
- 2011/11/06: added 'extra' nominal 60Wp south-facing ground-mounted panels to off-grid SLA-charging circuit as the system has missed coming out of low-power mode a couple of times in the last week or so. One of the panels seems to be effectively dead (~2Voc or less) but the others are still showing a respectable 16--23Voc, so swapped in separate 15W panel of same dimensions from nearby (though its rear glass plate is cracked and so performance is probably below nominal) and replaced that with a new Maplin N70JK 15W with metal stand.
- 2011/09/10: wired old 40Ah gel into main battery bank, direct to MPPT controller via long-ish cable and self-resetting thermal fuse with aim of it being slightly-higher impedance route than to main bank, thus avoiding 40Ah taking too much strain in parallel with much newer ~400Ah set.
- 2011/08/20: ADSL modem back on-grid as SLA voltage getting low.
- 2011/08/13: currently getting about 0.2V drop on 12V line upstairs powering ADSL modem (~9W measured) and 0.1V drop powering server (@~4W).
- 2011/07/25: moved connection of 36Wp amorph panels (at front) to main charger/battery in part to help keep ADSL off-grid for now and to simplify setup. Older 40Ah gel may optionally be paralleled with new bank, possibly via own fuse. (Old 40Ah gel at 13.23Voc today, 2011/09/10 12:00 GMT ~25°C ~13.2Voc.)
- 2011/07/11: fitted Morningstar Remote Temperature Sensor (RTS) to MPPT controller to help protect the LA battery bank. Fixed the sensor to the -ve lug of a battery in the middle of the bank: have thermally insulated it (with an old sponge as it happens) from the air to ensure that it reflects battery core temperature as accurately as possible.
- 2011/07/04: ADSL off-grid again; 0.20V drop from controller battery terminals to bus upstairs near power take off for modem at 12.78V (bat).
- 2011/04/22: found and fixed wiring problem which had smallest (2Wp) panel reversed and fighting against 60Wp winter panel set, so not contributing to SLA input.
- 2011/04/22: moved 12Wp panel from LiFePO4 to SLA input so former is dumping less and latter is full more, ie better balancing.
- 2011/04/16: wired in dump load (currently only ~16R/15W) for LiFePO4 battery.
- 2011/04/15: adjusted turbine crowbar trip to 18V, ie above max output voltage from LiFePO4 battery and below Voc of the PV inputs, so presumably 'safe' for the BMS input, to try to reduce spurious and potentially damaging repeated operation a little when the battery is full.
- 2011/04/11: took down (60Wp amorphous) 'winter' solar panel set.
- 2011/04/10: experimentally taking ADSL router off-grid using lap-top adaptor (previously using mains via same adaptor). Initially until 2011/05/12 when battery getting a bit low.
- 2011/01/14: rearranging system to accommodate new SLA bank.
- 2010/11/20--2010/11/21: inserting 30A automotive 'MAXI' fuse into SLA +ve connection to Morningstar controller, then next day 20A in load side from controller, thus SLA side voltage reading glitches to 0V, while LiFePO4 side keeps the SheevaPlug running.
- 2010/10/11: moved MotorWind turbine over-voltage crowbar circuit to outside junction box and plumbed output via blocking diode to secondary/LiFePO4 array circuit, ie any wind power now charges the LiFePO4 battery unless already full.
- 2010/10/11: disconnected wind-power-available sensor (Input3).
- 2010/10/11: split main PV (motley) array into two isolated parts, in particular the lower-voltage Uni-Solar triple-junction (Voc ~ 17V) is now in the section feeding the LiFePO4 battery.
- 2010/10/11: added 100Wp mono panel to main off-grid PV array.
- 2010/10/09: upgraded battery voltage sensing to include second battery and reduce noise, and improve accuracy using external 50kΩ trimpots.
- 2010/10/05: added LiFePO4 12V 20A battery to system fed from a sub-set of the panels and powering the SheevaPlug from a diode-OR with the normal SLA output.
- 2010/10/01: now reducing sampling rate (to no more than one sample each 10 minutes from previous sample each even minute) if battery voltage/SoC very low so as to save energy associated with the sampling, logging to disc, etc...
- 2010/09/30: reconnection of approx 60Wp of south-facing ~70°-tilt panels as battery crept down to 'amber' at controller (<12V) after several successive gloomy days, plus other minor reconfiguration for robustness/winter.
- 2010/04/05: temporary removal of approx 60Wp of south-facing ~70°-tilt panels now battery is reaching float every day and turbine 'emergency brake' is repeatedly operating!
- ~2009/10/15: addition of approx ~72Wp of south-facing ~70°-tilt amorphous panels from Maplin.
- ~2009/09/21--2009/10/03: major reconfig with laptop off battery, SheevaPlug
permanently on battery, battery voltage measured via analogue input rather than
via two opto digital inputs (LVD/high), and solar controller(s) being upgraded
to a single Morningstar MPPT.
- 2008/07/01 (~0900UTC) new laptop/server internal battery fitted.
- 2008/06/26 Input1 NOW UNALLOCATED; no longer 'DC-DC converter output OK'. Current allocation/meaning of inputs:
- "Battery Voltage High" (Input0) reports essentially when the battery is full and still charging, so the system should dump some energy.
- "LVD Output On" (Input2) reports when the battery is fairly full and is running the server/laptop.
- "Wind Power" (Input3) reports when a turbine is turning, though not necessarily generating useful energy.
- 2008/06/24 laptop internal battery died so 2008/06/26 replaced mains/off-grif switchover mechanism with an 'instant' diode-based scheme.
- 2008/06/05 (~1600UTC) rewiring to reduce impedance and improve behaviour under heavy load.
- 2008/06/01 (~1700UTC) addition of 2x12Wp amorphous panels (Maplin N32CX, TopRay TPS-102-12) on east-facing near-flat porch roof, bringing off-grid total to ~120Wp.
- 2008/05/24 (~1200UTC) addition of 12Wp amorphous panel (Maplin N32CX, TopRay TPS-102-12) on east-facing near-flat porch roof (in place of 13Wp test panel).
- 2008/05/24 (~0700UTC) addition of tiny 2.4Wp (Maplin N59FU, Nikkai) amorphous panel on west-facing near-flat shed roof.
- 2008/05/10 (~1430UTC) to 2008/05/24 (~1200UTC): temporary/intermittent addition of 13Wp horizontal PV on east side of house to catch morning sun and extend off-grid period for server.
- 2008/04/17 (~0800UTC) to 2008/04/23 (~1100UTC): major rewiring.
- 2008/04/10 (~2000UTC): disconnection of 2x1W turbines for wiring rearrangement.
- 2007/12/01 (~1600UTC): installation and connection of MotorWind 8-turbine device.
This page was automatically generated on 2014/07/21 UTC (Mon Jul 21 12:13:36 UTC 2014).
Copyright © Damon Hart-Davis 2009. [home]